|FA12167||Can we use a line supply of 230VAC (Phase and Neutral) in Altistart 48 to supply a 230VAC, three phase motor.|
Altistart 48 is unable to work on a single phase supply (Phase and Neutral), even if you disable the PHF (loss of line phase) fault.
|FA22662||What is the principle of operation for Magnetic Latching Contactor CR1F.|
The latching function is due to the magnetic circuitry used in CR1F** contactors.
There are two inputs on the coil
Input to latch the contactor...
|FA22656||Is it possible to mount a surge suppressor with LED (LAD4RCE) on the CA4KN**, low consumption DC control relay.|
CA4KN** control contactor comes fitted with integrated surge suppressor (bidirectional diode), thus there is no need for an external surge suppressor.
|FA22595||Which are the materials used in Compact NSX connection terminals.|
The material used in the Compact NSX terminal connectors is as below:
Compact NSX100-250 : Copper (Cu) + Tin coating
|FA12160||What is the maximum cable length allowed for connection of the Remote display of the Altivar 71 Drive.|
The maximum cable length allowed for connection of the Remote display of the Altivar 71 Drive is 10 Meters.