|FA279789||Higher Charging Voltages for C-Series Charge Controllers|
Need to know how to charger higher than 15V/30V/60V in bulk without changing the nominal battery voltage.
C40, C35, C60
|FA12173||How to unlock the access of all Drive Parameters in Altivar 31 Drive.|
In order to gain access to all the Altivar 31 Drive parameters one of the two conditions will apply:
1. Parameter Access Via Standard Keypad (Integrated...
|FA272010||What causes a CONE fault code on an ATS22 softstart?|
What causes a CONE fault code on an ATS22 softstart.
ATS22, Altistart 22
|FA253002||What does the strolling LEDs mean on the ATV312?|
What does the strolling LEDs mean on the ATV312?
Altivar 312, Altivar 12
All serial numbers
|FA12064|| How to change page resolution in configured project of Vijeo Citect.|
S In order to change the resolution of the pages in Vijeo Citect project do following things: 1. Add the following INI parameter through...
|FA22780||What is the minimum interval between two consecutive overloads of 150% for 60 seconds for ATV31 Series Drives.|
The 150% overload time is specified as 1 minute (60 sec) every 10 minutes at 40°C ambiance temperature. This means that the ATV31 Drive is allowed...
|FA22775||How many UA150 ATS controller can be used with one DC150 module.|
Only one UA150 controller can be used per DC150 and its Digipact address must be set at 14-14.
|FA12104||What is the internal wiring connection of Motor Mechanism Module (MT100 to MT630) for Compact NS <630 MCCB range.|
Refer the attachment for the internal wiring connection of Motor Mechanism Module (MT100 to MT630) for Compact NS
|FA22774||What are the characteristics of STR13MAE (MAE500) trip unit used in Compact NS630 circuit breaker.|
The Compact NS630 fitted with the STR13MAE trip unit is named: NS630MAE500.
The old MA500 trip unit was designed with mechanical feature. The new...
|FA12072||What is the overvoltage fault threshold of Altivar 31.|
The over voltage fault threshold of Altivar 31 is as attached.