|FA12165||What is the Line dip Ride Through time for the Altivar 71 and Altivar 61 Drives.|
Maximum running time (without fault) at Under Voltage with Nominal Torque is: 1. 1000 msec. with a voltage 70% of nominal voltage (UrEs). 2. 500msec....
|FA22631||What is the reference of Type A or Type B thermostat in Prisma Plus switchboard.|
Type C thermostat is available in Prisma Plus, the part reference of which is 08998. The Type C thermostat Reference 08998 can be used as Type A or...
|FA22637||What are the specifications of CRa, CRb & CRc sensors used in SM6 circuit breaker with their part references.|
Refer the below table for the specification of the sensors:
Note: CRa/CRb/CRc sensors are not commercialized components. These sensors are...
|FA22638||What is the amount of SF6 gas in 24 kV SF Circuit Breaker range.|
In 24 KV SF Circuit Breaker range, the weight of the SF6 gas per pole for different Circuit Breakers is as follows:
SF1 Type 1 – 49 grams
|FA22632||Does Prisma Plus Switchboard confirm the Electrical continuity of moving parts.|
The Prisma Plus confirms the electrical continuity of moving parts as per IEC/EN 60439.1
Find attached the Declaration of Conformity for the same.
|FA12164||What is the maximum operating altitude for Altivar 71 Drives.|
Altivar 71 Drives are designed to operate for altitude up to 3000 Meters.Note: The maximum operating altitude is 1000 Meters, after which you have...
|FA22615||What is the thermal class temperature for coil of CT Contactor.|
The thermal class temperature for coil of CT contactor is 180 Degrees Centigrade.
|FA22627||Can impulse-type power supply be used for electrical opening and closing order of Compact NS MCCB. |
Yes, the impulse-type power supply (time duration > 20 ms and Voltage level above 0.7Un) can be used for electrical opening and closing of Compact...
|FA22628||Is it possible to get the Earth Fault alarm only without tripping in Compact NSX with Micrologic 6, via Modbus communication.|
Yes, only the Earth Fault alarm can be achieved in Compact NSX with Micrologic 6A/6E without tripping the MCCB at Earth Fault.
For this, Ground...
|FA12200||What is the maximum rated current for 36KV Fusarc switch.|
The maximum rated current for 36KV Fusrac switch is 63 Amps. Refer attachment for the selection of proper fuse.